Shandong real-name exposure has fire safety illegal behavior and hidden dangers
Time to keep the fire hidden dangers, Shandong Traditional Chinese Medicine (Jinan) 1, the fire source (not seting fire pool) is not set in accordance with national engineering technical standards; 2. Setting up indoor fire hydrant systems in accordance with national engineering standards 3, the automatic water sprinkler system (indoor fire hydrant system and automatic sprinkler system) without the national engineering technical standards (indoor fire hydrant system and automatic water injection fire extinguishing system do not set fire hydrant pump, spray pump, pump adapter, high water tank and related regulator facilities), Only 5, 6 floors in the medical technology building have automatic sprinkler system, the other floors are not set); 4 Smoke facilities do not meet the technical standards); 5 Automatic alarm system does not function properly; 7, anti-smoke system, fire-fighting pump, etc. Caving the fourth layer of color steel plate; 10, the stairway between the gallery and the ward building, the depth of the ladder is insufficient, the form of the stairry does not meet the requirements; 11. The southwest stairs of the medical technology building are not enough; 12 The wall of the stairway is not blocked. "The unit is actively rectifying, and it is expected that the reform of December is completed.
Qingdao Bank School (Qingdao) 1, there is no indoor fire hydrant in the restaurant, violating the provisions of Article 16 of the Fire Protection Law of the People’s Republic of China; 2, dormitory building, No. 6 building does not set machinery Smoke facilities, violates the provisions of Article 16 of the Fire Law of the People’s Republic of China; The second provisions of the second paragraph; 4, the outdoor fire hydrant is not set, violates the provisions of Article 16 of the Fire Protection Law of the People’s Republic of China. Zibo Jinglu Petrochemical Storage and Transportation Sales Co., Ltd. (Zibo City) 1, the first floor of the office building is safe export, the second floor of the 25th floor evacuation indication logo is not in line with national standards; 2. No fire control room value record, fire prevention inspection record; electrical appliance The line is regularly maintained, and the detection has no record; the micro-fire station data desk is not revised; the fire file is not prepared;
Yao Chunzhi life supermarket (Zaozhuang City) 1, indoor fire hydrant water supply pressure; 2. Some electrical line laying does not meet the standard; 3. Training drill record is not standardized; ability. Lijin County Teng Yun Restaurant (Dongying City) 1, the number of fire extinguishers in the store is insufficient; 2. Existing fire extinguisher is not kept intact;
Antai International Hotel Property Management Co., Ltd. (Yantai) 1, no fire truck is set up; 2, the fire control cabinet cannot be associated with other automatic fire protection facilities; 4, automatic water sprinkler system failure, no normal use; 5, fire automatic alarm system fault, no normal use; 6, no smoke protection facilities in the corridor, the smokeless facilities have not been operated normally; 7, fire door damage The rate is greater than its standard requirement to set the total number of 50%; 8, the fire control indoors are not arranged in duty. Weifang Changyi Municipal Golden Peacock Entertainment Plaza (Weifang City) personnel intensive places are settled in colored steel clamping panels, and the combustion performance level of color steel clamp core material is lower than that of national standard 8624 specified. Jining Aijia Property Management Co., Ltd. (Jining City) The fire alarm system fault in Guanya Xingcheng Community, which is managed by the property company, and cannot be used normally. Xintai City Sanqiang Department Store Co., Ltd. Trinity Home Appliance Mall (Taian) 1, no closed stairwell; 2, a layer of evacuation walkway set rolling door; 3, the second floor window is blocked by the billboard; 4, indoor fire hydrant water supply Insufficient stress, it is not normal to use.
Weihai Gaoshen Tourism Leisure Products Co., Ltd. (Weihai) 1, fire-fighting central control room no person duty; 2, fire control cabinet stop, fire automatic alarm system is closed; 3. Indoor fire hydrant system in the factory disabled, The indoor fire hydrant has no pressure water; 4, the water pump room fire pump, the spray pump is deactivated, the automatic water sprinkler is closed, can not immediately return to normal operation; 5, canteen kitchen dynamic area is not effective with other regions Fire protection separation; 6, the generator is not effective fire-resistant separation on the water pump room evacuation channel and is in a deactivated state.莒 县 中心 中心 (Rizhao City) 1, the first floor of the office building is safe export, the second floor, the evacuation indication mark setting does not meet the national standards; 2. No fire control room value record, fire inspection record; electrical product line regular maintenance No record without recording; not a timely revision of micro-fire station data desk account; not preparing fire files; Yucheng County Pengcheng Printing Co., Ltd. (Linyi City) 1, the production workshop did not set up the stairwell as required; 2. The second floor of the production workshop lacks safety exports; Fire hydrant; 5, the indoor fire hydrant is not set as required; 6. The production workshop is built using flammable materials.
Wangquan County Wangquan Building Hotel Second Store (Dezhou) 1, the hotel lacks a scattered staircase; Outdoor fire hydrant is not set.县 孝 老年 公 有限 有 公司公 公司 (城) 1, two, three layers lack of evacuation stairs; 2, two-storey indoor fire hydrant water; 3. Fire automatic alarm system deactivated; 4, fire control room value staff Fire Control Room Operates a Vocational Qualification Certificate. Huimin County Hu Ji Town Oriental Red Business Hotel (Binzhou) 1, no closed evacuation stairway; 2. The safe export width in the hotel does not meet the requirements; Billboard occlusion.
Shandong Zhongjia Furniture Co., Ltd. (Heze City) 1. Production workshop did not set automatic water sprinkler system and fire automatic alarm system in accordance with the fire protection technical standards; 2. The parameters of the fire hydrant pump do not meet the demand for fire protection, and no spare pump is set. Satisfaction with one preparation requirement. (Shandong Fire Contribution) (Editor: Public Snow, Xing Manhua) Sharing Let more people see the recommended reading.